8 Jul electrical specifications of ASTM F . Ground cable assemblies shall have an ampacity greater than or equal to that of No. 2 AWG copper. ASTM Standard F was originally written with the intent of covering temporary protective grounds to be used on overhead power lines. The standard was bas. Abstract– During implementation of a maintenance program that was intended to check compliance of field grounding devices with ASTM F, field personnel.
|Published (Last):||16 July 2004|
|PDF File Size:||14.74 Mb|
|ePub File Size:||15.47 Mb|
|Price:||Free* [*Free Regsitration Required]|
Not Logged In Member?: ASTM does not give any warranty express or implied or make any representation that the contents of this abstract are accurate, complete or up astm f855 date. If a protective ground installed in an equipotential arrangement astm f855 too much resistance, it will not protect workers.
See Appendix X2 for details. Ferrule Types Ferrules are categorized according to ferrule-to-clamp connection method and by either shrouded or nonshrouded. Training for the Qualified Em The above current values are based on electromechanical test values. The clamps shall be subject to astm f855 tests for determining mechanical torque strength and electrical short circuit capacity. Most of the cables in the market are constructed to ASTM standards and have performed well in utility use.
At present, there is no Type II specification. F8555 meet ASTM standards, temporary personal protective grounds must use multistranded flexible cable conductor installed in a rated clamp using protective cable ferrules.
However, astm f855 assembling qstm, care should be taken to maintain conventional similarity of metals in the electrical connection to minimize connection corrosion. With the exception of Asstm 7 in astm f855 ultimate astm f855, all grades of clamps exceed the matching grade ground cable fault current ratings for the 6-,and cycle durations under the derated scenarios.
Wednesday, 21 February Train the Trainer Clamp types I and II are for installation on conductors that astm f855 been de-energized and tested. Type III is usually installed astm f855 a formed T-handle and is intended as a first connection to a system neutral, pole bond, or grounded station or apparatus steel that does not require use of a hot stick.
Class B clamps have serrations or crosshatch patterns on the contact surface intended to abrade or bite through corrosion products on the surface of the conductor. Astm f855 1 to Grade 7 Clamps Clamp grades 1 through 7 establish minimum requirements for physical strength astm f855 electrical characteristics in withstand rating, ultimate rating and continuous current, strength yield and ultimate strength.
In addition, the paragraph notes that many of these cables have been tested to the ASTM standard and have been found to meet the requirements of the standard.
Referenced Documents purchase separately The documents listed below are referenced within the subject standard but are not provided as part of the standard. Such calculation also astm f855 that the resistance between the station and the point of a fault will further limit the amount of power delivered into the fault. The nonthreaded stud astj of an ASTM-rated ferrule is always half-diameter size for each grade even though each grade of ferrule corresponds to a specific cable size.
Construction of complete assemblies of protective astm f855. After 25 years as a transmission-distribution astm f855 and foreman, Asmt Vaughn, CUSP, has devoted the last 20 years to safety and training.
If the cable is not compliant with astm f855 ASTM standard, the insulation may be too thick to astj under the ferrule shroud. The narrow part of the sleeve is the cable connector that is crimped onto the conductor strands. Over astm f855 duration of the fault, the components heat up and the ratings of the components decrease.
This standard does not purport to address all of v855 safety concerns, if any, associated with its use. Continuous current ratings for ASTM-rated grounding-type cable is as follows: You can change your cookie settings through your browser.
Astm f855 Appendix X2 astm f855 details. After 25 years as a transmission distribution lineman and foreman, Jim Vaughn has devoted atsm last 15 years to safety and training. About Testing Grounds assembled by the employer require continuity integrity testing and inspection in order to comply with